NUTUPSDRV(8)

NAME
nutupsdrv - generic manual for unified NUT drivers

SYNOPSIS
nutupsdrv -h
nutupsdrv [-a id] [-d num] [-x var=val] -k device
nutupsdrv [-a id] [-x var=val] device

DESCRIPTION
nutupsdrv is not actually a driver. This is a combined man page for the shared code that is the core of many drivers within the Network UPS Tools package. For information on the specific drivers, see their individual man pages. In general, all UPS drivers provide a communication channel between the UPS attached on device and the upsd daemon. The driver's task is to pass to the upsd process information about the UPS state and parameters. The core has two modes of operation which are determined by the command line switches. In the normal mode, the driver will periodically poll the UPS for its state and parameters. The results of this command is presented to upsd. The driver will also handle setting variables and instant commands if available. The driver can also instruct the UPS to shut down the load, possibly after some delay. This mode of operation is intended for cases when it is known that the UPS is running out of battery power and the systems attached must be turned off to ensure a proper reboot when power returns.

NOTE
You probably don't want to use any of these options directly. You should use upsdrvctl(8) to control your drivers, and ups.conf(5) to configure them. The rest of this manual describes options and parameters that generally are not needed by normal users.

OPTIONS

-h  display an help message without doing anything else. This will also list possible values for -x in that driver, and other help text that the driver's author may have provided.

-a id
    autoconfigure this driver using the id section of ups.conf(5).

-d num
    wait additional num seconds after receiving the shutdown command in shutdown mode before turning off power to the load. Also configurable via "sddelay" in ups.conf(5).

-k  ("kill" power) Force shutdown mode. The UPS will power off the attached load if possible. You should use upsdrvctl shutdown whenever possible instead of calling this directly.

-x var=val
    define a variable called var with the value of var in the driver. This varies from driver to driver - see the specific man pages for more information. This is like setting var=val in the ups.conf(5), but -x overrides any settings from that file.

device
    The /dev entry corresponding to the TTY the UPS is connected to. This is optional if you are using the -a autoconfiguration option, since the "port" entry in the ups.conf(5) will be used when available.

DIAGNOSTICS
Information about the startup process is printed to stdout. Additional messages after that point are available in the syslog. The ups clients such as upsc(8) can be used to query the status of a UPS.

PROGRAM CONTROL
You should always use upsdrvctl(8) to control the drivers. While drivers can be started by hand for testing purposes, it is not recommended for production use.

FILES

ups.conf(5)
    Required configuration file. This contains all details on which drivers to start and where the hardware is attached.

BUGS
Some of the drivers may have bugs. See their manuals for more information.

SEE ALSO

  Server:
upsd(8)

  Clients:
upsc(8), upscmd(8), upsrw(8), upslog(8), upsmon(8)

  CGI programs:
upsset.cgi(8), upsstats.cgi(8), upsimage.cgi(8)

  Drivers:
apcsmart(8), bcmxcp(8), belkin(8), bestferrups801-807(8), bestfortress(8), bestuferrups(8), bestups(8), cyberpower(8), dummycons(8), dummyups(8), etapro(8), everups(8), fentonups(8), genericups(8), hidups(8), hp(8), isbmex(8), liebert(8), masterguard(8), mge-ellipse(8), mge-utalk(8), microdowell(8), newapc(8), oneac(8), powercom(8), powernet(8), sec(8), sms(8), snmp-ups(8), tripplite(8), victronups(8)

  Internet resources:
The NUT (Network UPS Tools) home page: http://www.exploits.org/nut/ NUT mailing list archives and information: http://lists.exploits.org/